Until the relay is activated, the contact remains in the 11-10 position. After the power voltage is supplied, contact is shifted to position 11-12 and the countdown of the preset value t is commenced. After the preset time t has been counted down, contact returns to position 11-10. The working sequence of the relay may be repeated after turning the power supply off and on.
* Setting the time range knob regulator in the:
ON - position with power supply activated results in the permanent closure of the contact in position 11-12.
OFF - position (power supply activated) causes the contact to be permanently closed in the 11-10 position.
* With the power supply on, the system does not respond to time range setting modifications.
* The newly set time range is active after the power supply has been turned off and on.
* With the power supply on, it is possible to regulate the preset time freely within the selected time range.
|Power supply voltage||230 V AC|
|Operating mode||lagged deactivation|
|The executive element||relay|
|Maximum load current||10 A|
|Contact configuration||1 ├Ś NO/NC|
|Separation of the contact||YES|
|Delay of operation||50 ms|
|Contact status indication||LED red|
|Operating time - adjustable||0,1 s ├Ě 576 godz.|
|Power indication||LED green|
|Terminal||pluggable terminal blocks 2,5 mm┬▓|
|Tightening torque||0,4 Nm|
|Power consumption||0,8 W|
|Working temperature||-25 ├Ě 50 ┬░C|
|Dimensions||1 module (18 mm)|
|Assembly||on rail 35 mm|
|Ingress Protection Marking||IP20|