* DELAYED OFF - CYCLIC
Until the relay is switched on, the contacts remain in positions 2-3 and 11-10. After applying the supply voltage, the contacts are switched to positions 2-1 and 11-12 for time t1. After measuring the time t1, the contacts return to positions 2-3 and 11-10 for the time t2. The sequence of these switching is carried out cyclically.
* DELAYED ANNOUNCEMENT - CYCLIC
After applying the supply voltage, the contacts remain in position 2-3 and 11-10 for time t1. After measuring the time t1, the contacts are switched to positions 2-1 and 11-12 for the time t2. After time t2, relay contacts return to positions 2-3 and 11-10. The sequence of these switching is carried out cyclically.
* When the power is turned on, the system does not react to changing the time range settings.
* Work with the newly set time range occurs after switching off and restarting the power supply.
* With the power supply switched on within the set time range, it is possible to smoothly adjust the time in the range of the time setting value.
|Power supply voltage||24 V AC/DC|
|Operating mode||cyclical work|
|The executive element||relay|
|Maximum load current||2 ├Ś 8 A|
|Contact configuration||2 ├Ś NO/NC|
|Separation of the contact||YES|
|Delay of operation||50 ms|
|Contact status indication||LED red|
|Operating time - adjustable||0,1 s ├Ě 576 godz.|
|Power indication||LED green|
|Break time - adjustable||0,1s ├Ě 576 godz.|
|terminal||screw terminals 2,5 mm┬▓|
|Tightening torque||0,4 Nm|
|Power consumption||0,8 W|
|Working temperature||-25 ├Ě 50 ┬░C|
|dimensions||1 module (18 mm)|
|Assembly||on rail 35 mm|
|Level of security||IP20|