The relay can maintain power for up to 10 minutes and switch the contact position after power failure.
A - MAINTAINING
Powering up of the relay is followed by the closing of the contacts (position 5-4/8-7). After power failure, the contact position is maintained for a set period of time. When the specified time is up, the contacts open (position 5-8/8-9).
B - DELAYED ACTIVATION
When the power voltage is switched on, contacts remain open (position 5-6/8-9) for the preset time. After that time contacts close (position 5-4/8-7) until power is off.
C - DELAYED ACTIVATION WITH MAINTAINING
When the power voltage is switched on, contacts remain open (position 5-6/8-9) for the preset time. After that time contacts close (position 5-4/8-7). After de-powering contact remain closed for a preset time. When the specified time is up, the contacts open (position 5-6/8-9).
* When the power is on, the system does not respond to changes in the setting of time and function.
* The new settings of functions and time are operation after power restart.
This product is no longer in stock
|Power supply voltage||12├Ě264 V AC/DC|
|Operating mode||with power suspension after power loss|
|The executive element||relay|
|Maximum load current||2 ├Ś 4 A|
|Contact configuration||2 ├Ś NO/NC|
|Separation of the contact||YES|
|Delay of operation||50 ms|
|Contact status indication||LED red|
|Operating time - adjustable||0,1s├Ě10 min.|
|Power indication||LED green|
|terminal||screw terminals 2,5 mm┬▓|
|Tightening torque||0,4 Nm|
|Power consumption||0,56 W|
|Working temperature||-25 ├Ě 50 ┬░C|
|dimensions||1 module (18 mm)|
|Assembly||on rail 35 mm|
|Level of security||IP20|