The controller can operate as an independent unit (designated for opening/closing one roller blind) as well as the controllers can be combined into groups that enable the central controlling of many roller blinds
The roller blind motor is activated by the momentary switching of a current pulse (L or N) to one of the control inputs. The motor is activated at a time programmed previously by the user. The activation time programmed enables the complete lifting or lowering of the roller blind. Also, there is a possibility of stopping the rolled blind activated at a level selected by the user (non-complete opening or closing of the roller blind).
Driver control inputs - one-button
Local control - a pushbutton connected to the terminal 5 controlling the one roller blind.
-upwards (opening) / downwards (closing).
Pressing the local control push-button activates the movement of the roller blind in a direction opposite to the direction of a previously performed movement (after connecting the controller to the power supply, the first movement closes the roller blind). If the roller blind is already moving, pressing the local control push-button will stop the roller blind movement. When the local control push-button is pressed again, the movement of the roller blind in the opposite direction is activated.
Central control - a common group of push-buttons connected to terminals 7 and 8 for many controllers (minimum two controllers) that controls all roller blinds included in the central control system.
- all upwards; - all downwards.
Pressing the central control push-button activates the movement of the roller blinds in a selected direction. If one of the roller blinds is already moving in the same direction, its movement will be continued. If one of the roller blinds is moving in the opposite direction, this roller blind will be first stopped and then its movement will be activated in the direction in accordance with the command sent to the central input.
The central control enables only activating the movement of the roller blinds in a selected direction. The roller blind will be stopped after the programmed movement time or when any of the local control push-buttons is pressed.
|Power supply voltage||24 V AC/DC|
|Engine type||230 V AC|
|Control signal||L lub N|
|Maximum current of the control pulse||1 mA|
|Maximum AC-3 load current||1,5 A|
|Switch-on time - programmable||0 s ├Ě 10 min.|
|The executive element||relay|
|terminal||screw terminals 2,5 mm┬▓|
|Tightening torque||0,4 Nm|
|Power consumption||1 W|
|Working temperature||-25 ├Ě 50 ┬░C|
|dimensions||1 module (18 mm)|
|Assembly||on rail 35 mm|
|Level of security||IP20|