MID Directive 2004/22/EC
A special electronic system under the influence of flowing current and applied voltage in each phase generates pulses proportional to the energy drawn in the respective phase. Energy consumption in the phase is indicated by a flashing of corresponding LED (A, B, C). The sum of the three phase pulses is indicated by a flashing LED and converted into energy absorbed throughout the three-phase system. Its value is displayed by the segment LCD display. The fractional digit represent the decimal (.1 kWh = 100Wh).
The meter is equipped with pulse output SO+ - SO-. This allows you to connect another pulse device (SO) that reads pulses generated by the meter.
No additional connected equipment is required for proper operation of the meter.
|Reference voltage||3├Ś400 V+N|
|Current current||10:00 AM|
|Maximum current||100 A|
|The minimum measured current||0,04 A|
|Accuracy of measurement in accordance with IEC61036||class 1|
|Counter's own consumption||10 VA; 2 W|
|Scope of indication of the abacus||0├Ě99999,9 kWh|
|Counter constant||(1,25 Wh/imp) 800 imp/kWh|
|Reading signaling||LED red|
|Pulse output SO + SO-||open collector|
|Connection voltage SO + SO-||max. 30 V DC|
|Connection current SO + SO-||max. 27 mA|
|Pulse time SO + SO-||34├Ě80 ms|
|Power consumption indication||3├ŚLED red|
|terminal||screw terminals 25 mm┬▓|
|dimensions||7 modules (122 mm)|
|Assembly||on rail 35 mm|
|Level of security||IP20|