The module is designed to work with current transformer with 5 A secondary current.
The module continuously measures the current flowing through the measurement input. Readout of recorded current strength, setting of all communication parameters are all carried out through RS-485 port using the MODBUS RTU communication protocol. Power up is indicated by a green LED U light. Valid data exchange between the module and the second device is indicated by a yellow LED Tx light.
The transducer measures the effective value of TrueRMS current, which ensures high accuracy even with distorted flow.
Reset communication settings
Under cover is available code switch.
Details of resetting available in the instructions below.
This product is no longer in stock
|Power supply voltage||9├Ě30 V DC|
|WE-WY breakthrough voltage||2,1 kV|
|Communication protocol||MODBUS RTU|
|The type of work||SLAVE|
|Speed ??- adjustable||1200├Ě115200 bit/s|
|Bits of parity||EVEN / ODD / NONE|
|Maximum measuring error||0,50%|
|Measurement range TrueRMS / maximum voltage||0├Ě15 A/285 V AC; 0├Ě20 A/400 V DC|
|Maximum power consumption||50 mA|
|Precision of reading the register||0,1 A|
|Sampling frequency||10 Hz|
|Relative air humidity (for 30||85%|
|terminal||screw terminals 2,5 mm┬▓|
|dimensions||1 module (18 mm)|
|Assembly||on rail 35 mm|
|Level of security||IP20|
Protocol parameters MODBUS RTU