BIS-412M 230 V
The receiver is activated after a current pulse that is triggered by pushing one optional momentary push-button belonging to the local control group. The contact of the relay is switched to the 7-10 position. After a next current pulse, the receiver will be deactivated (the contact of the relay returns to the 7-12 position).
DEACTIVATE ALL - after a current pulse triggered by pushing the momentary push-button , all receivers will be deactivated (regardless of their status, i.e. deactivation or activation) that are controlled separately by individual relays. The contact in each relay will be switched to the 7-12 position.
ACTIVATE ALL - after a current pulse triggered by pushing the momentary push-button , all receivers will be activated (regardless of their status, i.e. deactivation or activation) that are controlled separately by individual relays. The contact in each relay will be switched to the 7-10 position.
The BIS-412M 230V is compatible with bell pushes equipped with fluorescent lamps.
This product is no longer in stock
|Power supply voltage||165├Ě265 V AC|
|Maximum AC-1 load current||16 A|
|The executive element||relay|
|Contact configuration||1 ├Ś NO/NC|
|Separation of the contact||YES|
|Resistance to shock currents||NO|
|Number of channels||1|
|Delay of operation||0,1 ├Ě 0,2 s|
|Control pulse current||less than 5 mA|
|Cooperation with illuminated buttons||YES|
|Status memory after power failure||YES|
|Activate on time||NO|
|Dedicated central control inputs||YES|
|terminal||screw terminals 2,5 mm┬▓|
|Tightening torque||0,4 Nm|
|Power consumption||0,7 W|
|Working temperature||-25 ├Ě 50 ┬░C|
|dimensions||1 module (18 mm)|
|Assembly||on rail 35 mm|
|Level of security||IP20|