MID Directive 2004/22/EC
A special electronic system under the influence of current flow and applied voltage in each phase, generates pulses in proportion to the electricity consumed in this phase. Phase energy consumption is indicated by flashing the corresponding LED (L1, L2, L3). The sum of the pulses of the three phases is indicated by a flashing LED shall be converted to energy, taken throughout the three-phase system, and its value is determined by the segment LCD display. Decimal represent the hundredths (.01 KWh = 10Wh).
The indicator has a pulse output SO+ SO-. This allows you to connect another device pulse-reading (SO) pulses generated by the counter.
For proper operation of the meter is not required to connect additional devices.
*) Base current - determines the current value at which the percentage measurement error is close to zero. If the current flowing through the meter is higher than the base current value, then the measurement error is negative, which works to the benefit of the electricity payer. On the other hand, if the current flowing through the meter is lower than the base current value, the percentage measurement error is positive and that acts against the electricity payer. These statements arise from metrological characteristics (percentage measurement error as a function of current), supplied to the user manual of a electricity meter. It is obvious that the meter measures electricity correctly with the meter accuracy class in the whole measurement range.
Maximum current - the maximum current for permanent load of the electricity meter.
Minimum current - the lowest value of the load current, which the meter detects and record.
Marking on the device: 5(63)A - position 1 (before the parenthesis): base current of 5A; position 2 (in parentheses): maximum current 63A.
This product is no longer in stock
|Compatibility||MID Directive 2014/32 / EU|
|Reference voltage||3├Ś400 V+N|
|Current current||5:00 AM|
|Maximum current||63 A|
|The minimum measured current||0,04 A|
|Counter's own consumption||10 VA; 2 W|
|Scope of indication of the abacus||0├Ě99999,99 kWh|
|Counter constant||(1,25 Wh/imp) 800 imp/kWh|
|Reading signaling||LED red|
|Pulse output SO + SO-||open collector|
|Connection voltage SO + SO-||max. 30 V DC|
|Connection current SO + SO-||max. 27 mA|
|Pulse time SO + SO-||35 ms|
|Power consumption indication||3├ŚLED red|
|terminal||screw terminals 16 mm┬▓|
|dimensions||4,5 moduleu (75 mm)|
|Assembly||on rail 35 mm|
|Level of security||IP20|