Special electronic system, under the influence of current flow and applied voltage, generates pulses in each phase in proportion to the electricity consumed in this phase. Energy consumption in phases is indicated by flashing LED A and C. The sum of the pulses of the three phases is indicated by flashing LED (800 imp/kWh) and is converted to energy consumed in the entire three-phase system, and its value is displayed by segment LCD display. The number after the decimal is tenths (0.1 kWh = 100 Wh).
Indicator has a pulse output SO + - SO.
Indicators can seal covers of input and output terminals to prevent making the bypass indicator.
|Reference voltage||3 x 400 V|
|Current current||10:00 AM|
|Maximum current||100 A|
|The minimum measured current||0,04 A|
|Accuracy of measurement in accordance with IEC61036||class 1|
|Counter's own consumption||10 VA; 2 W|
|Scope of indication of the abacus||0├Ě99999,9 kWh|
|Counter constant||(1,25 Wh/imp) 800 imp/kWh|
|Reading signaling||LED red|
|Pulse output SO + SO-||open collector|
|Connection voltage SO + SO-||max. 30 V DC|
|Connection current SO + SO-||max. 27 mA|
|Power consumption indication||2 x LED red|
|terminal||screw terminals 25 mm┬▓|
|dimensions||7 modules (122 mm)|
|Assembly||on rail 35 mm|
|Level of security||IP20|